Standard Specification for Hubless Cast Iron Soil Pipe and Fittings for Sanitary and Storm Drain, Waste, and Vent Piping Applications
This specification covers hubless cast iron soil pipe and fittings for use in gravity flow applications. These pipe and fittings are intended for non-pressure applications, as the selection of the proper size for sanitary drain, waste, vent, and storm drain systems allows free air space for gravity drainage. The pipe and fittings shall be iron castings suitable for installation and service for sanitary, storm drain, waste, and vent piping applications. The pipe and fittings shall meet all applicable requirements and tests given in this specification. Tensile test and chemical test shall be made to conform to the requirements specified. The pipe and fittings shall be uniformly coated with a material suitable for the purpose that is adherent, not brittle, and without a tendency to scale.
1.1 This specification covers hubless cast iron soil pipe and fittings for use in gravity flow applications. It establishes standards covering material, manufacture, mechanical and chemical properties, dimensions, coating, test methods, inspection, certification, and product marking for hubless cast iron soil pipe and fittings. These pipe and fittings are intended for non-pressure applications, as the selection of the proper size for sanitary drain, waste, vent, and storm drain systems allows free air space for gravity drainage.
1.2 The EDP/ASA numbers indicated in this section represent a Uniform Industry Code adopted by the American Supply Association (ASA). A group designation prefix, 022, is assigned to hubless products, followed by the four-digit identification assigned to individual items and a check digit. This system has been instituted to facilitate EDP control through distribution channels, and is to be used universally in ordering and specifying product items. Those items with no EDP numbers are either new, special, or transitory and will be assigned numbers on subsequent prints of this specification.
1.3 This specification covers pipe and fittings of the following patterns and applies to any other patterns that conform with the dimensions found in Tables 1 and 2 and all other applicable requirements given in this specification.2
EDP/ASA Identification Numbers for Hubless Pipe
10 ft (3.0 m) in sizes and 5 ft. (1.5 m) 11/2 , 2, 3, 4, 5, 6, 8, 10, 12, and 15 in.
Fig. 1, Fig. 2
Method of Specifying Fittings
Quarter Bend, Reducing
Quarter Bend, with Side Opening
Quarter Bend, with Heel Opening
Quarter Bend, Tapped
Quarter Bend, Double
Quarter Bend, Long
Long Sweep, Reducing
Eighth Bend, Long
Sanitary Tee with Side Opening
Sanitary Tee with 2 in. Side Opening R or L/R and L
Sanitary Tee, New Orleans Special with Side Opening
Sanitary Tee with 45° Side Openings and New Orleans
Sanitary Special Tee Tapped
Sanitary Tapped Tee, Horizontal Twin
Sanitary Tapped Tee, Double Vertical
Y Branch, Double
Y Branch, Upright
Upright Y Wide Center Florida Special
Y Branch, Combination 1/8 Bend
Y Branch, Combination 1/8 Bend Double
Sanitary Cross with Side Opening
Sanitary Cross, New Orleans, with Side Openings
Sanitary Cross, New Orleans, with 45° Special and Regular Side Openings
Sanitary Cross, Tapped
Tapped Extension Piece
Iron Body Cleanout, Tapped
P Trap, Long
P Trap, Deep Seal
P Trap, with Primer
P Trap, with Tapped Inlet
Tapped Inlet, Double
Modified Combination Wye and 1/8 Bend, Double
Modified Combination Wye and 1/8 Bend, Double, Extended
Closet Bend, Regular and Reducing
Closet Flange Riser
Double Sweep Sanitary Tee (Extended)
Running Trap with Double Vents
P Trap with Tapped or Hubless Side Inlet
Vented Tub Wye Extended, Double
Vented Tub Wye Extended Offset, Left or Right
Vented Tub Wye
Double Two-Way Cleanout
1.4 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.5 The committee with jurisdiction over this standard is aware of another comparable standard published by the Cast Iron Soil Pipe Institute, CISPI 301.
Note 1: The text of this standard references notes and footnotes that provide explanatory material. These notes and footnotes (excluding those in tables and figures) shall not be considered as requirements of the standard.
1.6 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
Formato físico y digital
Nota: Precios sin IVA ni gastos de envío
Añadir a la cesta